Reduced Outage Time
“To maximize the profitability and efficiency of electricity grid operators through cost reducing and timesaving solutions for fault finding, surveillance, remote control and automation of distribution grids”
Com. Unit for Integration With NorTroll or Third Party RTU
Communicates with 1 – 12 line mounted indicators Communicate with the RTU on MODBUS
Short range radio; 2,4 GHz
Range up to 30-50 meter Remote Indication
12 VDC power
Communication Between Linetroll and Comtroll 115
The rotary switch on the ComTroll 115 called “ADDRESS” should be set to the number of indicators used in this location, in this case ‘3’.
Able Integration with any type of RTU Modem’s supported by Digital Input and Output.
The indicators will in PtP mode operate one individual relay output on the ComTroll 115C each. The Communication failure/Low Battery relay on the ComTroll 115C will be activated if one or more the three indicators send this message.
The FDP-15 can be used as a radio interface to a collector or fault indicator when sending configuration data to the unit.
FDP-15 have also a memory where parameters for different types of fault indicators and collectors can be stored. The memory can store one set of parameters for one type of field device of the following type;